Updated: Dec 20, 2019
In this case study, our structural engineering team in Perth assisted with a retaining wall inspection in the Perth Hills.
The limestone retaining wall was constructed to support a concrete swimming pool on the high side. The construction of retaining walls or any foundation requires special considerations on a clay site. In this particular case, the design did not include control joints to allow for movement due to soil being affected by seasonal moisture conditions. This has resulted in cracks up to 20mm wide.
The solution consisted installation of control joints, fixing the cracks and re-pointing sections of the retaining wall. While it was difficult to saw cut across the entire width of the retaining wall, it was deemed that this solution should be adopted due to being relatively cost effective.
If you have any questions about structural engineering inspections or pre purchase structural building and pest inspections in Perth, get in touch with us to discuss your requirements and to obtain a free quote.
Go beyond excellence with RBC!
Rotaru Building Consultants
send us an email
call us: +61 432 043 518